have you mastered the correct operation of the burst generator
different from other products, the pulse group generator is specially designed according to the characteristics and requirements of electrical and electronic products for electrical fast transient pulse group test. it has the characteristics of good reliability, stable performance, convenient use and so on. so how to carry out the correct operation when we operate it? today, let’s talk about the correct operation instructions of the burst generator
first of all, before the use of the burst generator, ensure that the fg terminal on the back of the generator is reliably connected to the reference grounding plate before the test. before starting the machine, turn the voltage setting knob counterclockwise to the bottom. when wiring before the test, the wiring should be carried out when the burst generator is not working. the test configuration and layout should be carried out according to the relevant standard requirements. check the wiring, and connect to the power grid after confirming that the wiring is correct, and then start the machine.
then, if you want to adjust the parameters of the pulse group (test voltage, polarity, etc.) during the test of the pulse group generator, you should press the “stop” key to stop the test, and then you can adjust it; in case of disassembly / wiring during the test, you should press the “stop” key to stop the test, and turn the voltage knob counterclockwise to the end before you can operate. i hope you can gain from the above knowledge